Check Out Our Work in Tarpon Springs FL
Apex Plumbing provides air conditioning, heating, water heater and plumbing services to the residents of Tarpon Springs, FL and the surrounding areas since 2018!
Read our reviews and find out why your neighbors consider us to be their nearby heating and air company and local plumber in Tarpon Springs, FL.
for Tarpon Springs, FL
Our Reviews by City
Old 1/2 hp effluent pump is not working Check wires to pump with voltage tester and the pump is receiving power I pulled the pump out and lifted the float switch straight up and pump will not turn on The tank the pump sits in is not sealed and the lid is in bad condition and need to be replaced with the pump Pump may be clogged with sewage We will replace effluent pump with a 3/4 hp grinder pump because effluent pump only pumps sewage and a grinder pump grinds sewage up before pumping it down the sewer line which greatly reduces chances of a clogged pump and with perform much better So we will install and new 3/4 Grinder pump and tank with a 3 year parts and labor warranty
Dig up and evaluate why grinder pump is not turning on
THIS IS AN L SHAPED SHOWER, AND WILL REQUIRE A CUSTOM PAN INCLUDING THE FOLLOWING: -REMOVE FLOOR -REMOVE PAN -REMOVE DRAIN AND REPLACE -TAKE TILE OUT 12 IN UP WALL -PAN WILL NEED PRE-SLOPED -INSTALL NEW CUSTOM PAN INCLUDES PERMITTING AND INSPECTIONS APEX IS NOT RESPONSIBLE FOR REPLACEMENT OF TILE 10 YEAR WARRANTY ON MATERIALS
Diagnose any issues with heater. Heater not getting power from electrical box on wall behind it.
Joes angle stop is compromised we have to cut it off the 1/2 in pvc and apply a new one therefore the leak will stop We have to shut off the water per repair
P trap gasket replacement
Client called in regards to a water leak. The slab he already has leak detection come out and locate the leak We have to cut the tile to access the concrete We have to cut and excavate the concrete slab in order to find the trouble area We will cut out the compromised area and do a spot repair on the compromised copper pipe using a pro press and copper pipe also copper pro press fittings 3/4 or 1-2 in copper fittings/pipe After we fix compromised area we will backfill and re-concrete the slab in order to fulfill the job We do not replace the tile
Cable through toilet in first bathrooms Cast iron pipes Feminine products got caught